Jackson and Son specializes in professional, 100% guaranteed residential and commercial heating and air conditioning installation, maintenance tune-ups and repair services.
Read what your Burgaw, NC neighbors say about our quality services, then call us at 919-734-9611 to schedule an appointment.
for Burgaw, NC
Our Reviews by City
2023 model Trane AHU 3 indoor coil frozen. No filter installed. No filter slot in AHU. Returns are fire dampers that cannot accept filter. Need to cut filter slot for AHU3. Tech allowed system to thaw while diagnosing other unit. 2017 model Goodman AHU 6 dripping into aux pan and draining from aux drain line. Kenny got pic July 19. 2023 model Carrier AHU 3 no filter installed. Installed 20*25 filter inside AHU. Trane 2010 model AHU 4 appears no longer on site. Carrier AHU installed 12 days ago. Tech found thermostat blank due to black line voltage wire not seated into polarized plug. Transformer only getting 120v. Seated plug. Programmed Vision Pro from factory startup. Allowed system to cool for 10 minutes without issue. Recorded pressures. Tested drain. Tested heat mode and defrost cycle. Returned to system 3 after getting system 4 cooling and ensured indoor coil is thawed out. Tech found true suction service port valve core leaking below switchover valve. Uploaded picture. Tighte
Unit #4: Dining Room
Upon arrival thermostat was satisfied tech did ensure blower motor was at high speed airflow was correct in vents maintenance man did mention dinning area unit is down and unit 3 is trying to cool that as well tech did educate if all units are not operating correctly then unit will not be able to keep up as needed
Upon arrival tech found drain line clogged up and kitchen hood vents were on, not allowing to cool off kitchen. Pressures were within spec. Tech flushed out drain line and informed maintenance personnel to turn off hood vents inside kitchen. System is back up and cooling.
UNIT #4 2022 MODEL CARRIER CONDENSER PAIRED WITH 2010 MODEL AMERICAN STANDARD AIR HANDLER. FOUND INDOOR TXV RESTRICTION. $1996.00 PLUS TAX FOR TXV. SPOKE WITH MR. CUPP. HANDED OVER TO COLBY FOR PROPOSAL ON AIR HANDLER.
SYSTEM #3 EVAPORATOR COIL IS LEAKING. SPOKE WITH MR. CUPP. TOPPED OFF WITH REFRIGERANT FOR TIME BEING. ALSO SPOKE REGARDING CAPACITOR THAT WAS RECENTLY REPLACED ON SYSTEM #3 THAT WILL BE WORKED INTO PROPOSAL. FORWARDED TO COLBY TO WORK ON PRICING FOR REPLACEMENT.
Unit #2 (Right Hall)
Tech preformed recommended repairs from previous service. Breaker for AHU#1 was already replaced upon arrival. Tech checked unit and system is operating correctly at this time. Tech replaced capacitors on AHU#5 and HP Cond#3. Tech has attached pictures to invoice. Units are operating at this time. Director expressed concerns about Lobby / office unit. Tech advised director that leaking coil was diagnosed from previous visit and estimates were being calculated for repair vs. replace.
Tech preformed CMA FULL SERVICE on 8 split systems. System 1 and 2 are both down at this time due to power challenges. System 3 is operating at this time but low on refrigerant due to leaking evaporator coil. All other systems are operating at this time. Tech has attached performance reports to invoice along with estimates for any minor repairs needed.
Full service on 3 Trane gas furnaces, AC systems, changed filters.