Jackson and Son specializes in professional, 100% guaranteed residential and commercial heating and air conditioning installation, maintenance tune-ups and repair services.
Read what your Goldsboro, NC neighbors say about our quality services, then call us at 919-734-9611 to schedule an appointment.
for Goldsboro, NC
Our Reviews by City
Richard - Goldsboro, NC 27534
The young man knew what he was doing u
RICHARDS - Goldsboro, NC 27530
NICK - Goldsboro, NC 27530
The tech was very polite and very knowledgeable about my service call.
THOMPSON - Goldsboro, NC 27534
Kenny was very efficient and helpful. It was a pleasure meeting and chatting with him. He did an awesome job servicing my equipment.
BURNS - Goldsboro, NC 27534
I couldn’t make sense of the report, generated with the new computer system.
NIMITS - Goldsboro, NC 27530
Matthew is a very good technician very polite. Does a job well and explains what he has done very well overall good hand thank you
JOHNSON - Goldsboro, NC 27534
Kyle diagnosed our situation immediately.
COMPOST - Goldsboro, NC 27530
Friendly tech. and very knowledgeable about unit
LEANN - Goldsboro, NC 27530
DREEZ - Goldsboro, NC 27534
ALTHOFF - Goldsboro, NC 27534
Luis was very professional and did a great job determining and fixing the problem with ductwork at our house. Well done!
Jackson and Sons Review
LOCUST - Goldsboro, NC 27534
LIVINGSTON - Goldsboro, NC 27530
Always professional techs and service. Goto company for all HVAC service
HARRIS - Goldsboro, NC 27530
Understood my thermostat issue and resolved it.
FAITH - Goldsboro, NC 27530
Called in at 7-30am, Jerry had Luis Rivera come. From the time I called, to completion was 1 1/2 hours.. that is fast service. Jerry always helps us and gets us taken care of fast. Luis did a wonderful job. Really knew what he was doing!!! Thanks again
HARRIS - Goldsboro, NC 27530
SMITH - Goldsboro, NC 27530
BENAISSA - Goldsboro, NC 27534
MAZUROWSKI - Goldsboro, NC 27530
Outstanding service and support!
TORAN - Goldsboro, NC 27530
Mr. Williams was very professional and provided outstanding service on my HVAC unit. His knowledge and expertise along with the rest of team is why I chose Jacksons & Son to service my unit. Thank you!
FELTON - Goldsboro, NC 27534
SALVATION - Goldsboro, NC 27530
Luis was polite, quick, and did a great job.
FLANIGAN - Goldsboro, NC 27530
Service was excellent! Kyle was awesome!
MCDOWELL - Goldsboro, NC 27534
He was pretty knowledgeable and very polite in doing his work. He said Norah was his name, I believe.
HOLLOWAY - Goldsboro, NC 27534
Very professional and excellent work.
Tech found unit would shut off when aux heat would engage tech found 2 pole 40 amp contactor was shorted causing unit to disengage and turn off once contactor would pull in tech quoted out for repair $255.47 customer approved tech replaced contactor unit started up no issues and would engage aux heat no issue
FOUND FAULTY ECOBEE TSTAT. REPLACED WITH TEMPORARY FP5000. NEED TO RETURN WITH WARRANTY ECOBEE.
Upon inspection tech found evaporator coil of upstairs system leaking in attic. Most of drain pan was covered in oil film from refrigerant as well as refrigerant lines had signs of oil film. Tech verified leaks with leak detector. Condensing unit compressor megged bad on all three windings. Tech also found indoor blower run cap testing weak. System is in bad shape, 30 years old. Field supervisor came out to determine best solution. Tech continued maintenance on downstairs system and found no challenges. Need to come back by when in the area to drop off a 14x24x1 and a 20x20x1.
Tech preformed esa maintenance per energy savings agreement tech found no challenges at todays visits system is heating and cooling properly at this time. Replaced 3 20x25x1 filters.
Performed ESA, informed costumer about having a plasma air purifier in the system for dust control, costumer would like to wait for now, he will eliminate some factors before investing in a plasma air purifier.
UNABLE TO DUPLICATE ANY ABNORMAL SMELLS. CYCLED BOTH SYSTEMS MULTIPLE TIMES. STATED SMELL IS NO LONGER THERE WHEN TECH ARRIVED. WILL NEED TO CALL IF CHALLENGES PERSIST. COILS HAVE BEEN TREATED WITH CLEANER.
Performed ESA. Recommended replacing UV Bulb but customer did not wish to do at this time.
PERFORMED PTU 1 SYSTEM. LENNOX PACKAGE HEAT PUMP. NEED TO RETURN AND REPLACE 5’ OF 6” FLEX. INVESTED IN PSA 1 SYSTEM.
Performed inspection on 8 gas furnaces/AC systems, 8 mini splits, 1 package unit, changed filters. #5, #6 condensers are 0 psi- missing 3/8 copper line set. #4 furnace and blower has low voltage short K36 relay is bad, 2A fuse blows. #7 T-stat missing cover. Estimate to move condenser to roof. Mini split #6 Estimate to move AH to south wall by door.
Tech was anbe to get entry into apartment tech found indoor coil frozen and found the compressor frozen as well tech pulled disconnect off of unit to ensure compressor would not engage and unit defrost will need to come back to check pressures at a later date
Tech preformed esa maintenance per energy savings agreement tech found 2 inch of water in drain pan tech drained out and vacuumed water tech found no challenges at todays visits system is operating correctly at this time.
Unit was missing 2 screws on compressor side door and 2 screws on electrical panel door where book mount is located tech replaced screws package heat pump s#154L
Replaced a variable speed blower motor on unit #8. Tested system in cooling. Delta T within specs (22). Pressures within specs. System is cooling as of now. Prices will be set by Ron.
Tech cleaned both systems thoroughly, found no challenges at this time. Both systems operating properly. Customer stated he would call into office if he decides to get back on service agreement.
Performed ESA on both systems. Customer was not home at time of maintenance. Filters left on front porch.
Tech preformed esa maintenance per energy savings agreement tech found no challenges at todays visits system is heating and cooling correctly at this time. Replaced 26x20x1 filter.
Tech is not picked up a smell upon arrival. Has 2 split systems for upstairs, tech Removed blower housings to inspect that nothing was trapped with it the heat strips or duct that would cause an abnormal smell. Return side of the evaporator coils are cleared, no obstructions where found. Tech picked up a scent of refrigerant from one of the systems at the evaporator coil with the electronic leak detector(system that operates the left side upstairs). Leak is not big enough to cause an ammonia/abnormal smell. Tech noticed some of the ceiling tiles were knocked out of place and suspects that the smell could possibly be coming from the attic, tiles were recently knocked out of place and is the first time the costumer has had an odor challenge. Tech sprayed deodorizer on both systems to neutralize any odors. Tech did inform costumer that if the smell comes back throughout the day, to immediately call us back. Business is closed and No CMA was recommended.
Tech cleaned system thoroughly, tech found indoor and outdoor coils very dirty. Tech changed filter at return, system is operating properly. Tech recommended changing filter more often and making sure to keep a clean filter in.
Tech preformed esa maintenance per energy savings agreement tech found no challenges at todays visit system is heating and cooling correctly at this time.
Tech washed and serviced unit Customer didn’t want to extend extended ESA, tech recommended all options for renewal
Need to reschedule per customer request
Customer stated the thermostat was blank. Tech found low voltage fuse blown. Inspection found wire the low pressure switch was chafed and shorted to sensing bulb of TXV. Tech repaired and secured the wire, replaced the fuse and system is back up. Warranty
Tech cleaned system thoroughly, found no challenges. System is operating properly.
Tech washed and serviced unit