Jackson and Son specializes in professional, 100% guaranteed residential and commercial heating and air conditioning installation, maintenance tune-ups and repair services.
Read what your Wake Forest, NC neighbors say about our quality services, then call us at 919-734-9611 to schedule an appointment.
for Wake Forest, NC
Our Reviews by City
PERFORMED CMA FULL SERVICE ON 2 DEHUMIDIFIERS 1 GAS UNIT, 1 SPIT SYSTEM AND 2 GAS PACK UNITS. ALL SYSTEMS PERFORMING PROPERLY.
19051546JA head pressure was high Schrader on high side port was leaking tech tighted port and cleaned both kitchen and lobby systems Lobby system had insulation fallen inside the system removed insulation while cleaning system. Checked for leaks on lobby system as well in case the description of problems was wrong. Closed back door during visit since units are not designed to cool the outdoors
Tech found the drain for the larger gas pack (kitchen) was completely clogged with algae and partially obstructed by a zip tie. Tech used water hose and shop vac to clean and clear drain trap and drain line. Partially removed drain pan from package unit to use shop vac and water hose to completely clean drain pan. Reassembled drain and closed up unit. System is back draining correctly. Manager on duty also reported front gutter dripping. There are no HVAC drains near that location. There is a tree that has likely clogged the roof gutter with leaves. Tech recommends cleaning gutter and sealing seam in the bottom of gutter where it drips. Not HVAC related. Manager on duty also reported dehumidifiers not getting power. Service history reports we confirmed the same on May 15. Tech ensured that dehumidifier breakers are on. Humidistat is lit up and reports humidity setpoint is satisfied. Humidistat is powered from dehumidifier. No batteries. Dehumidifier is operational. Said registers in
Replaced blower motor and cleared drain line .
Performed inspection on 3 TRANE units, 2 Dehumidifier, changed all filters. Emptied condensate pump of water, found no power at dehumidifier outlet. Possible bad blower at AH #3 (restrooms). Left case of 20x20x1 filters.
Found coil to gas furnace froze up. Will need to de ice coil to further diagnose Immediately turned heat on and de iced coil Found system low on 410a Homeowner does not want new system at this time. Added 2 pounds 12 oz system is back to cooling properly
Tech preformed CMA FILTER CHANGE. All filters changed.