Jackson and Sons has provided full-service residential and commercial heating and air conditioning installation, maintenance tune-ups and repair services in Atlantic Beach, NC since 1974.
Read our reviews to learn why your neighbors call us first for their home and business comfort needs in Atlantic Beach, NC, then call us at 919-734-9611 to see what we can do for you.
for Atlantic Beach, NC
Our Reviews by City
PALM - Atlantic Beach, NC 28512
Charles - Atlantic Beach, NC 28512
Technician was very professional and focused on his work. Jackson and Sons provides outstanding service!
Performed ESA, homeowner extended ESA. Recommended surge protection.
Wiring was correct, no improper wiring was found. Line voltage was being sent to the fan motor. Tech initially believed the fan motor had failed. Traced the wiring ll the way to the fan motor and found a burnt plug connection at the compressor compartment which is a quick disconnect for the fan motor. Water may have slipped inside the connection since it is located on a area where water can get in. Tech spliced the wires to the condenser fan motor, tested cooling afterwards and system came back on without challenges. Condenser fan motor is rated for 1.1 amps and it was pulling 9amps. System is Back operating. Service warranty per Jerry.
Tech services unit and after service tech noticed thermostat blank tech got thermostat to come on system made loud popping noise and cut off tech reset breaker and inspected all wires and system cut back off. Tech was able to get system to come back on but outdoor fan no spinning. Tech smelled burnt rubber smell. Tech diagnosed our door fan failed another tech with fan will step out and replace motor. Tech believes motor was starting fail already as motor pulled somewhat high amps and motor is very rusty
PERFORMED CMA FULL SERVICE ON 3 SPLIT SYSTEMS. ALL SYSTEMS WORKING PROPERLY.
Tech performed ESA maintenance on Trane split system. Replaced 20*20*1 standard non pleated filter in hallway with regular filter. Per Brandon, customer prefers media filter. Tech brought 20*25*3. The correct size is 20*20*3. Will need to return to install media filter for previously quoted price. Cleaned indoor coil and drain with water and nitrogen. Found no challenges with indoor unit. Inspected outdoor unit and cleaned carefully with brush due to no outdoor water access on roof. Outdoor unit is clean and free of debris, copper, aluminum and sheet metal surfaces show corrosion due to salt air. Capacitor, amp draws, and refrigerant pressures are within specs. Tech recommends customer clear out all items from HVAC and water heater closet. Boxes and items may block airflow or get wet in case of drain backup. Tech recommends removing items from auxiliary drain pan under air handler to prevent wet items from getting wall or floor wet in case of drain backup. Tech recommends not usin
JACOB AND JUAN REPLACED A TRANE SPLIT HEAT PUMP
Tech found unit
Performed cma inspection on 3 split system air handlers. All systems operating correctly at this time.
Filter change on 3 Goodman air handlers.
Tech is servicing a LG mini split system.
Inspect 3 Goodman AH, 3 Geothermal pumps, changed filters.
Cma full service