Jackson and Son specializes in professional, 100% guaranteed residential and commercial heating and air conditioning installation, maintenance tune-ups and repair services.
Read what your Edenton, NC neighbors say about our quality services, then call us at 919-734-9611 to schedule an appointment.
for Edenton, NC
Our Reviews by City
Upon arrival customer stated system number 3 Vision Pro 8000 thermostat was locked out with an unknown passcode. Tech removed code lock per customer request. System is operating properly. This was not a recently replaced thermostat. Billing out to Lumenant for service call fee.
-Complete repairs as approved prior: -Install EZ trap and insulate at 4 air handler locations. -Insulate drain pipe at 1 air handler location. -Replace blower motor capacitor at 2 air handler locations. -Resecure ductwork insulation at air handler 7. -Replace outdoor fan motor capacitor at 4 condenser units. -Found system 4 off at thermostat. Verified 24 v at thermostat location. Recommend replacement of thermostat. Provided estimate $652.32. Spoke with Scott for on site approval.
Replaced indoor Txv system back to cooling
Performed cma full service on 9 split systems, 2 exhaust fans, and 1 make up air unit. System 1: Air handler leaking condensation from cabinet. Found cabinet not level, causing condensation to collect at return side of drain pan and leak out of cabinet instead of exiting via drain line. Recommend leveling of cabinet. Price for labor to be estimated by office. Condenser unit outdoor fan motor capacitor tested weak. Provided estimate for replacement of capacitor $196.98. System 2: No access to clean existing condensate drain line trap. Recommend addition of EZ Trap to properly service drain line. Provided estimate for installation of EZ Trap $138.12. AHU-2 Air handler blower motor capacitor tested weak. Provided estimate for replacement of capacitor $202.65. Condenser unit outdoor fan motor capacitor tested weak. Provided estimate for replacement of capacitor $196.98. System 4: No access to clean existing condensate drain line trap. Recommend addition of EZ Trap to properly service dr
System 2 not cooling due to bad thermostat wire and thermostat. Tech swapped g for black and changed faulty thermostat. System back to cooling suspect clogged drain due to water under system System 3 ( 23124NGY3V) we installed the July 14 2023 was cooling upon arrival this unit serves the nurse station Tech wrote 3 on thermostat. AHU 5 has issue with smoke detector relay , was bypassed upon arrival . Tech verified relay way bad. Serves dinning room Will need Smoke detector company to replace parts and troubleshoot smoke detectection system for unit 5 trane serial ( 183450AN3v) Unit 5 needs a new indoor txv ( 183450AN3v) will also need a 16cu in biflow filter dryer. Unit 4 living room Serial number F221204691 unit drain pan was full of water. Unclogged unit and system back to cooling System 3 which is a new unit which serves front nurses station was cooling as it should, only reason it could not keep up. System 9 serial 23122tkt4f kitchen unit was low on charge. Tech add
Middle Hall Intersection/Reception Unit
Right Wing Unit
KITCHEN SYSTEM, LEFT HALLWAY SYSTEM, RIGHT/MIDDLE HALLWAY SYSTEM FOUND ALL (9) TOTAL 30A CONDENSER DISCONNECTS BLOWN DUE TO (3) FAILED COMPRESSORS. EXTREMELY COSTLY REPAIRS ARE NOT RECOMMENDED. COLBY IS SENDING PROPOSALS FOR EQUIPMENT REPLACEMENT. SPOKE WITH MR. CUPP.