Jackson and Son specializes in professional, 100% guaranteed residential and commercial heating and air conditioning installation, maintenance tune-ups and repair services.
Read what your Grantsboro, NC neighbors say about our quality services, then call us at 919-734-9611 to schedule an appointment.
for Grantsboro, NC
Our Reviews by City
Performed a full service maintenance on 3 Goodman package AC. Changed filters. Cleared drain lines.
Unit #9: Dining Room
Unit #2: Bathroom/200 Hall
Tech returned to complete approved repairs. Tech installed new drain line on system #8 and added primary float switch per agreement. Tech replaced auxiliary float switch for system #8 aswell. System is back up and operating and draining correctly. Tech replaced condenser fan motors on systems # 4 & #10. Systems are operating correctly at this time. Tech also replaced blower capacitor and fan capacitor on system #11, system is operating correctly at this time. Tech replaced fan capacitors on systems #1, #3, & #5. Units are up and operating correctly at this time. Director asked tech to look at system #7, stating it was not cooling. Tech called office for approval to diagnose system while at location and was giving approval to proceed. Tech found condenser unit #7 not operating. Unit had low voltage call at contactor, but no high voltage was present. Tech traced loss of power back to disconnect were tech found there was no power to disconnect on line side. Tech checked main panel box but
Tech found unit number 10 on high-pressure lock out. Tech reset And tested unit operation to the best of ability due to rain. Refrigerant pressures appear to be within specs. Tech has a -20 delta t. Indoor and outdoor fan motor are working properly. No issues found at this time
Tech preformed CMA FULL SERVICE on 11 split systems and 3 mini splits systems. Tech has attached all performance reports to invoice along with recommended repairs. Tech has attached estimates for recommended repairs as well. Tech recommends replacing systems 6 and 9 and mini split #2 due age and cost of repairs.