Jackson and Son specializes in professional, 100% guaranteed residential and commercial heating and air conditioning installation, maintenance tune-ups and repair services.
Read what your Hertford, NC neighbors say about our quality services, then call us at 919-734-9611 to schedule an appointment.
for Hertford, NC
Our Reviews by City
Replaced evap coils on mini splits 4 and 5
Unit #8: Front Lobby/Offices
Unit #4: Activity Room
Tech replaced 4 fan run capacitors, one transformer, and one contactor. Tech was able to confirm system 5 is back operational at this time and is cooling. Tech also installed float safety switch on system 4, however upon inspection tech found a fault with system 4 smoke alarm and system will not pass power with alarm in circuit. Tech did confirm without smoke alarm system will run as designed. Tech left smoke alarm in circuit for safety concerns. Tech has attached pictures to this invoice.
Tech replaced compressor for unit 9 System back to cooling. Replaced drain pan in unit 7 will need insulation for drain trap.
Techs preformed CMA FULL SERVICE on 14 split systems, 8 mini splits systems, 1 Air makeup, and 1 Exhaust Fan. Split System #8 and Split System #4 are down due to being void of refrigerant from leaking evaporator coils. Tech recommends replacing systems. Split System #9 is down due to compressor being shorted to ground. Tech recommends replacing compressor. Split System #5 is down due to low voltage short and failed transformer. Tech recommends locating short and replacing transformer. Split System #2 operates but has failed freeze stat interrupting compressor call. Recommend replacing freeze stat. Split System #7 operates but has crack in primary drain pan allowing water to leak into cabinet and auxiliary drain pan. Auxiliary pan float switch has failed, tech recommends replacing primary drain pan and auxiliary float switch. Split System #11 is down due to leak in line set and being void of refrigerant. Tech recommends replacing line set. Mini Split Systems #4 and #5 are not cooling pr