Jackson and Son specializes in professional, 100% guaranteed residential and commercial heating and air conditioning installation, maintenance tune-ups and repair services.
Read what your Leland, NC neighbors say about our quality services, then call us at 919-734-9611 to schedule an appointment.
for Leland, NC
Our Reviews by City
Tech replaced CMA filters at return tech found no challenges at todays visit.
Tech preformed CMA FULL SERVICE on 17 split systems. Systems 6, 12, 14, and 17 are all in need of replacement. System 5 needs electrian to diagnose power issue to air handler, further information is on system performance repot. All other units are operating at this time but need some repairs. Tech has attached system performance reports and estimates for any needed repairs.
Tech preformed CMA INSPECTION on 6 split systems and 1 mini split system. Tech found kitchen/ dining unit completely froze up from compressor, line set to evaporator coil. Issue has been previously diagnosed as mismatched R22 condenser unit to R410 air handler. Tech recommends replacing system with matching equipment. Tech also found the third floor air handler with multiple issues. Evaporator coil is extremely rusted and shows signs of refrigerant leak in coil. Blower wheel is extremely dirty and rusty. Recommend Replacing system due to system being R22 system. Tech found the gym system air handler evaporator coil extremely rusted with possible refrigerant leak. Tech also found a weak capacitor on condenser unit. Tech recommends replacing system due to system being R22 refrigerant. Upon inspection of laundry/office unit tech found dual run capacitor weak on fan side and low on compressor side. Tech documented and will attach estimate to invoice with replacement costs. Office will
Changed filters, cleaned grilles.
Full Cma service
Tech is servicing a Haier split system.
Full system tune up
Cma inspection and filter change on 7 split units