Jackson and Son specializes in professional, 100% guaranteed residential and commercial heating and air conditioning installation, maintenance tune-ups and repair services.
Read what your Morrisville, NC neighbors say about our quality services, then call us at 919-734-9611 to schedule an appointment.
for Morrisville, NC
Our Reviews by City
ANTHONY AND CHRIS
Tech found newly installed RTU3 kitchen unit cooling normally. Tech applied anti corrosion treatment to both micro channel coils and allowed to dry for 30 minutes per instruction on can. Restored power to new kitchen unit. RTU2 had a 24 volt call from thermostat for cooling, but neither blower, fan motors, nor compressors are running due to ESTOP switch open. Bypassed ESTOP for testing. Circuit 2 compressor has been converted from R22 to MO99 R438A and has only 90 psi of standing pressure. No liquid refrigerant. Circuit 2 holds 13 lbs of R22. Confirmed circuit 2 nearly void of MO99. Circuit 1 runs, but tech estimates circuit about 10 lbs low on R22. Holds 25 lbs of R22. Leak searching RTU2 would be $367.49. Repairing system would take 38 lbs of R22. System replacement is recommended. Tech found ESTOP on RTU1 open as well. Tech bypassed for testing and found system cooling normally. R22 pressures are in specs on circuit 1. Circuit 2 has been converted to MO99 and appears to be cool
QUEST 155 DEHUMIDIFIER
Kitchen Unit- Trane 17.5-Ton Gas Pack
WE WILL BE REPLACING FAILED DEHUMIDIFIER. FORWARDED INFORMATION TO COLBY.