Jackson and Son specializes in professional, 100% guaranteed residential and commercial heating and air conditioning installation, maintenance tune-ups and repair services.
Read what your Stella, NC neighbors say about our quality services, then call us at 919-734-9611 to schedule an appointment.
for Stella, NC
Our Reviews by City
Tech replaced dual run cap per homeowners satisfaction Compressor start and run winding weak System is back to cooling for now
Tech returned and replaced failed start kit. Recovered 1 lb 8 oz of remaining R22 in system. Flowed nitrogen while brazing in new indoor coil and filter drier. Threaded in new indoor TXV and tightened with two adjustable wrenches. Pressure tested to 200 psi nitrogen. System passed standing pressure test and soap bubble test. Evacuated system to 200 microns. System passed 20 minute standing vacuum test. Recharged with 5 lbs 10 oz of R22 plus 4 oz for 30 foot lineset. Tested system without challenges. Tech collected for repairs. Customer placed both split systems on regular Comfort Plus plan. First visit in 6 months.
Tech found 1.5 ton Trane split system for the bonus room to be running on arrival. Tech confirmed blower, outdoor fan motor, and compressor are amping normally. Tech found system not cooling due to being significantly low on R22 refrigerant. Factory charge is 5 lbs 10 oz. Tech estimates system 4-5 lbs low. Tech let customer know that we can perform a leak search and leak repair, but due to cost of R22 leak repairs and EPA phase out of R22 refrigerant, tech would recommend replacing system instead. To get system temporarily cooling by charging up system, tech quoted $998.86 including tax. Tech also found Trane start kit failed. Quoted $393.10 including tax to replace start kit to ensure compressor starts under peak load. Customer approval leak search. Tech swept outdoor unit and found no refrigerant leaks. Tech found indoor coil leaking near the center bottom Ubends on the door side of air handler. Uploaded video of detected location. Due to advanced corrosion, repair to existing in